Note: If necessary, please use the comments area below to further explain why a listed precaution cannot be taken in the manner described.
Available sprinklers, hose streams, and fire extinguishers are in service and operable.
Hot Work equipment is in good repair.
Fire detection equipment protected from false activation and damage.
PPE is used to protect worker from physical hazards while performing Hot Work.
Within 35 feet (11 meters) of work:
Flammable liquids, dust, lint and oily deposits are removed.
Explosive atmosphere in area is eliminated.
Floors are swept clean.
Combustible floors are wet down, and covered with damp or fire-resistive sheets.
Other combustibles are removed when possible. Otherwise, fire-resistive tarpaulins or metal shields are used.
All wall and floor openings are covered.
Fire resistive tarpaulins are suspended beneath work.
Ducts and conveyors that might carry sparks to distant combustible material are protected or shut down.
Work on walls, ceilings, and or roofs:
Construction is noncombustible and without combustible covering or insulation.
Combustibles on both sides of walls, ceilings, roofs are moved away.
Does not apply.
Work on enclosed equipment:
Enclosed equipment is cleaned of all combustibles.
Containers have been purged of flammable liquids/vapors.
Pressurized vessels, piping and equipment are removed from service, isolated and vented.
Does not apply.
Fire Watch/Hot Work area monitoring:
Fire Watch will be provided during and for at least 30 minutes after work (including lunch and any break times).
Fire Watch is supplied with suitable fire extinguishers and fire fighting equipment.
Fire Watch is trained in the use of fire extinguishing equipment and in sounding emergency alarm.
Fire Watch may be required in adjoining areas, above and below.
Fire Watch will verify isolated fire detection equipment returned to normal operation.
Other Precautions Taken: